PRODUCT - XLPE Power & Control Cable
|WHY XLPE CABLE ?|
Thermoplastic Power Cable (i.e. PVC Power Cable) ever since its introduction in low tension distribution network in mid - sixties failed to satisfy utilities and industrial users because of its may inherent limitations such as low power rating, poor emergency overload capacity, poor resistance to surge currents, thermoplastic nature , comparatively poor insulation resistance, shorter life with susceptibility to thermal degradatiuon, and though claimed to be moisture resistant absorbed considerable amount of moisture on long time exposure to lower the dielectric properties alarmingly. Utilities voidced their grievances in many forums agaisnt thermoplastivc cables which they were forced to use because of ban imposed by the Government on use of PILC cable in distribution network due to high import content of this cable.
M/s SUYOG ELECTRICALS LTD., decided to introduce XLPE Cable for Medium and Low voltage distribution network to provide utilities and industrial users a cable which combines the advantages of PILC and PVC Cables totally eliminating their demerits. Total installed cost of this cable is also much lower than that of PILC or PVC Power Cable. This cable is totally indigenous as XLPE' compound is now being manufacture by SUYOG ELECTRICALS LTD. in their newly installed modern microprocessor controlled compounding plant.
In fact 1.1 KV XLPE Cable is the most economic solution for low tension power distribution
with high efficiency and total reliability . Utilities and industrial users will
find in this cable a realisation of their ling elusive dream of an ideal cablke
for low tension power distribution system.
|Advantages of XLPE cable as compared to thermoplastic cable are listed below:
These cables are manufactured and tested as per national / international standards and also as per specific requirement of customer. Dimension of cables conforming to IS:7098/(Part-1)/1988 are given in table 4 to 12.
|Comparative data for current ratings and voltage drop/amp/m for 1.1 KV XLPE and PVC Power Cables are given in table - 13 under standard conditions. From this it will be observed that for equivalent power rating one size lower 1.1 KV XLPE cable may be used as substitute for PVC cable provided slightly higher voltage drop can be tolerated. Current rating, short circuit rating and rating factors for 1.1 kv XLPE Cable are given in Table 14 to 22|
|JOINTING AND TERMINATION|
|No special skill is required for jointing and termination of 1.1 KV XLPE cable.
For jointing and termination any of the following standard methods may be employed:-
|Cables can be overloaded upto max conductor temperature FOR 130 degree C for a duration of max 100 hours in any twelve consecutive months, and max. 500 hours during the life time of cable.|
|Besides being ideal for general purpose distribution 1.1 KV XLPE cable will be specially advantageous for use in steel plants, power station wiring, chemical plant wiring, under water wiring, wiring for mines etc.|
|NOTE OF CAUTION|
|Do not use PVC sheathed cables where it is likely to come in contact with sulphuric acid , highly chlorinated hudro carbon cresylic acids, pyridine, ketones & caprolactum.|
|We welcome enquiries on cable engineering problems and get them solved for you through our design and development staff and assist you in providing even design for cables to suit your particular requirement.|
|Click Below for Detailed Technical Specification Tables|